Goedhart ZFB (blow-through) or Goedhart ZFZ (draw-through), ceiling mounted industrial air coolers for cooling and freezing applications.
The Goedhart ZFB/ZFZ range is part of our industrial series. The advantage: A very high degree of customization is evident. Circuits matched to application give great performance and the optimized heat exchanger geometry have a greater specific output of the heat exchanger.
This High Performance Air cooler is available for both air flow directions (draw-through and blow-through). As a result, the Goedhart ZFB/ZFZ can be flexibly and effectively designed for individual refrigeration requirements – especially for complex applications.
The coil blocks have steel tubes and steel fins hot dipped galvanized and are suitable for NH3, CO2 and Coolants as a cooling medium. All evaporator coils are pressure tested to 40 bars and supplied with a light overpressure charge. Standard refrigerant connections are positioned on the left hand side of the unit when looking with the direction of the airflow.
|Engineering level||Industrial products|
|Application||Cooling & Freezing|
|Number of types||406|
|Capacities NH3||3,2 – 75 kW (NH3 pump System – SC2)|
|Capacities CO2||2 – 70 kW (CO2 dx – SC2)|
|Capacities Coolant||3,4 – 95 kW (E-glycol 37% tl1=5°C tin=-7°C tout=-4°C)|
|Fan diameter||450, 500, 560 and 630 mm|
|Max. number of fans each aircooler||4|
|Air configuration||blow-through (Goedhart ZFB) draw-through (Goedhart ZFZ)|
|Suitable||for NH3 pump System and other coolants|
|Fin spacing||6, 8, 10 and 12 mm|
|Tube material||Steel, hot dipped galvanized|
|Fin material||Steel, hot dipped galvanized|
|Mounting||The flush mounting protects against and prevents accumulation of dust and dirt|
|Sheet material||Casing material of galvanized sheet steel|
|Finishing||neutral (not spray painted)|
|Refrigeration Connections||Standard positioned on the left hand side of the unit when looking with the direction of the airflow|
|Connection/Header side||Protection by removable end covers, easy removed for maintenance|
|Drip tray||Hinged drip tray prepared|
|Fixing defrost||Defrost by hot gas spiral or electric defrost elements will be fixed to the bottom side of the coil|