The Goedhart BR50/BR50XF blast freezers are a range of floor mounted air coolers specially designed for quick freezing of food products with a best performance due to special tubes.
Shock freezing foodstuffs is technically extremely demanding on air coolers. The Goedhart BR50/BR50XF blastfreezer meets these demands effortlessly.
The technical specifications covering the cooling surface, the air volume, the finned piping system and the distribution of the refrigerant have all created benchmarks and guarantee the reliability of the process.
The process of quick freezing is very important to minimize the weight loss and conserving the qualities of the food product. The nutritional value is maintained, as well as the original taste. The fans on this range of air coolers have respectively standard 50 and 100 Pa external pressure available to enable the quick freezing process. A lot of possible optional extras are available.
This range is part of our customized industrial series. The coil blocks have stainless steel 304 tubes expanded into fully collared aluminium fins. A good thermal contact is achieved by expansion of the tubes into the fin collars, that are also utilised as spacers to provide a constant distance between the fins. All coolers are pressure tested to 40 bar (lower by cooling mediums) and are supplied with a light over pressure charge of dried air. Suitable for NH3/CO2- pump system and de system and the most coolants.
|Engineering level||Industrial products|
|Number of types||12|
|Capacities NH3||21 – 117 kW (NH3 pump System – SC2)|
|Capacities CO2||15 – 94 kW (CO2 dx – SC2)|
|Fan diameter||630 mm|
|Max. number of fans each aircooler||6|
|Suitable||NH3/CO2/H(C)FC pump System and DE System and the most coolants|
|Fin spacing||7, 10 and 12 mm|
|Tube material||Stainless steel 304 15 mm|
|Mounting||Floor- or ceiling|
|Material||galvanized sheet steel|
|Finishing||neutral (not spray painted)|
|Protection bends and headers||By removable cover plates|
|Defrost||hot gas spiral or electric defrost elements will be fixed to the bottom side of the coil|